- Disk shelf DS2246 reports
UT WARNINGalerts and after a while the warning gets auto corrected.
[FAS-01: statd: monitor.shelf.warning:warning]: Fault reported on disk storage shelf attached to channel 0a. Check fans, power supplies, disks, and temperature sensors.
[FAS-01: monitor.shelf.fault.ok:info]: Fault previously reported on disk storage shelf attached to channel 0a has been corrected.
[FAS-01: monitor: monitor.globalStatus.ok:info]: The system's global status is normal.
Element Status Status Bytes Status Descriptions
1: NONCRITICAL 03,00,18,01 UT WARNING
2: OK 01,00,24,00
3: OK 01,00,2A,00
4: OK 01,00,3D,00
5: OK 01,00,28,00
6: OK 01,00,3D,00
7: OK 01,00,2B,00
8: OK 01,00,2A,00
- Though the temperature in the Data Center is normal, the warning is generated daily and goes back to normal state after some time.